Replacement for Biral Urinal Controler US 89, US92, BS 01 R and BS 01 K
UTR13 was developed as the urinal controller US 89, US 92, BS 01 R and BS 01 K were discontinued by Biral, the pump supplier. Those controllers work with a conductive urinal control system. The device detects the conductance of the water over electrodes in the syphon of the urinal. The conductance decreases as soon as urine enters the syphon of the urinal. When the switching threshold is reached and the set waiting time has lapsed, the UTR activates the magnet valve over a semiconductor outlet and so triggers the flushing process. This reduces water usage to a minimum and the flush is only activated when it is necessary. This technology is viewed as proven on the market and is very popular especially in public buildings, since the control system functions completely sealed, and it is 100% vandal-proof.
Open PDF version…
For requests please contact our Support at email@example.com